Pseudomonas, Cryptosporidium, Legionella…What Germs Lurking in Swimming Pools and Spas Should you Watch Out for?
Several microorganisms are responsible for gastrointestinal diseases
Cryptosporidium is a parasite frequently found in swimming pools.
Its high tolerance to chlorine is due to its protective shell which allows it to survive for 7 days in a pool water treated with chlorine (1 ppm minimum).
It causes diarrhea and all the associated symptoms (headache, dehydration …) while Norovirus and Shigella can make swimmers sick with acute gastroenteritis.
Some virulent strains of E. coli are also responsible for the occurrence of gastroenteritis, but also urinary tract infections, meningitis, or sepsis
Pseudomonas aeruginosa and Legionella pneumophila are frequently found in hot water
Among the other infections, Pseudomonas aeruginosa is generally harmless except in immunocompromised patients where it can cause various urinary, cutaneous, pulmonary, eye infections …
Legionella pneumophila is responsible for disorders such as Pontiac fever but can also cause a fatal pneumonia, especially in immunocompromised patients, the elderly as well as young children.
According to a US study  based on 493 pools, between 2000 and 2014, 6 out of the 8 deaths recorded on the 27,219 swimming pool related infections were attributable to legionella.
What individual practices can help reduce the risk of infection?
A number of recommendations can be applied to avoid risks such as :
- Not swallowing the water.
- Not swimming in case of diarrhea.
- Checking chlorine concentration with test strips.
- Showering before getting in.
- Avoid crowded swimming pools.
In addition, public spas and pool managers must ensure that treatment levels (chlorine, bromine, etc.) constantly remain above a certain threshold.
They must perform tests several times a day to detect any unusual concentration of pathogenic microorganisms.
In addition to the aforementioned germs, pathogenic staphylococci, mycobacteria and amoebae should be investigated in water.
Continuous treatments are not enough to eradicate all germs from swimming pools. However, awareness of good practices has helped stop the progression of infections caused by Cryptosporidium.
Increased risk of legionella in hot tubs and spas, especially in hotels
High temperatures in hot tubs allows bacteria to thrive and constant water agitation may cause the evaporation of a certain amount of disinfectant.
As more people use spas, the amount of organic matter such as sweat, dead skin or urine tend to exceed the neutralization capacity of treatments.
Bubbles generate aerosols and if water is contaminated with legionella, human infection by inhalation becomes possible.
An increasing number of hotels feature swimming pools and Jacuzzi & whirlpool facilities.
This supports the findings of a 2018 study based on 1,079 cases of Legionnaires’ disease in European spas that showed that 10 out of 22 outbreaks originated from hotel settings.
Special regulations and guidelines in terms of legionella monitoring
In addition to pool basin water, the major risk points in terms of legionella proliferation in swimming pools are located in showers and whirlpools.
Facility managers have a major preventive role in this regard: they must ensure that the concentration of legionella in domestic hot water systems does not exceed 1000 CFU/L at all points in the network.
In addition, it is necessary to carry out regular water analyses and ensure that the hot water exceeds 50 °C throughout the system to prevent legionella proliferation.
Penalties may arise in case of risk management negligence and the facility may be closed by authorities in the event of a positive control.
Legionella resistance implies the need for regular monitoring through preventive testing
Today, legionella is the most alarming germ in swimming pools and spas as it is difficult to get rid of in the long term.
A 2019 European study based on 357 hotels that implemented corrective measures following a positive diagnostic to legionella showed that 25% of them had at least one new case of legionellosis in the two following years. 42% of these were located in Italy, 17% in Spain, 14% in France and 7,6% in Greece.
Compliance with regulatory requirements is not sufficient to effectively control the risk of legionella proliferation.
Fortunately, major advances in preventive testing do exist.
Rapid detection kits that can be used by any facility manager allow for optimal responsiveness and ability to adapt treatments depending on the actual concentration of legionella in water.
They also enable a multi-year tracking so users are able to timely adjust maintenance patterns upon early signs of proliferation and avoid widespread colonization.
Beauté J; The European Legionnaires’ Disease Surveillance Network. Legionnaires’ disease in Europe, 2011 to 2015 [published correction appears in Euro Surveill. 2017 Nov;22(46):]. Euro Surveill. 2017;22(27):30566. doi:10.2807/1560-7917.ES.2017.22.27.30566 https://www.ncbi.nlm.nih.gov/pmc/articles/PMC5508329/
France Bleu, St-Cyr-sur-Loire : la piscine municipale ferme pour suspicion de légionelle, 13 juillet 2019, https://www.francebleu.fr/infos/societe/st-cyr-sur-loire-la-piscine-ferme-pour-suspicion-de-legionelle-1563000450
 Hlavsa MC, Cikesh BL, Roberts VA, et al. Outbreaks Associated with Treated Recreational Water — United States, 2000–2014. MMWR Morb Mortal Wkly Rep 2018;67:547–551. DOI: http://dx.doi.org/10.15585/mmwr.mm6719a3
Legifrance, Arrêté du 7 avril 1981 relatif aux dispositions techniques applicables aux piscines, Version consolidée au 23 juillet 2019, https://www.legifrance.gouv.fr/affichTexte.do?cidTexte=JORFTEXT000000673968
Leoni E, Catalani F, Marini S, Dallolio L. Legionellosis Associated with Recreational Waters: A Systematic Review of Cases and Outbreaks in Swimming Pools, Spa Pools, and Similar Environments. Int J Environ Res Public Health. 2018;15(8):1612. Published 2018 Jul 30. doi:10.3390/ijerph15081612 https://www.ncbi.nlm.nih.gov/pmc/articles/PMC6121464/
Ministère de la Santé et des Sports, Direction générale de la Santé, CIRCULAIRE N°DGS/EA4/2010/289 du 27 juillet 2010 relative à la prévention des risques infectieux et notamment de la légionellose dans les bains à remous (spas) à usage collectif et recevant du public http://circulaire.legifrance.gouv.fr/pdf/2010/07/cir_31557.pdf
Susceptibility of hospital patients results in a case-fatality rate reaching up to 40 to 80% in...
Hospitals, retirement homes and clinics serve vulnerable populations, highly exposed to the most...
Municipalities took steps with heat to limit effects of record temperatures Just like in Poissy, a...